Dairy Plant-Wide Control System Upgrade in Less Than 3 Days
Perishable food products, especially in a high-volume, low-margin industry segment, cannot tolerate unexpected delays during the process cycle. Maintaining fresh, high quality product is a must, especially in dairy. For a large dairy manufacturer in the United States, maintaining consistency and absolutely no unplanned downtime is a constant concern.
The objective of this project was to eliminate the risk of production going down as a result of a failed obsolete component of the control system coupled with no system backup and no means of technical support. This would be accomplished by converting six (6) remote racks and 800+ I/O points to a new control platform, integrating a new production server, upgrading network infrastructure, and updating control system documentation.
Our team was also limited to an on-site cutover window of three (3) days for the entire process and CIP control system. Additionally, the “Engine Room [Boiler and Compressors]” could not be shutdown nor interrupted whatsoever.
To accommodate additional CIP functionality, we split PLC-5 code into two separate PLC’s, adding extra room to grow as the plant is updated and modified.
The 3-Day On-Site Cutover window was the most challenging component of the project. Pre-planning made all the difference in this project. To greatly increase the probability of success it was decided to:
1. BEFORE THE CUTOVER
Coordination of Malisko Team Members, network installation team, hardware install team and plant management.
Pre-assemble, pre-wire, power-up, configure and test ALL control system components including the 1771-to-1756 I/O chassis assemblies and I/O modules, ControlLogix processors, FTViewSE Server and three (3) Clients.
Server and PLC Configuration
Off-Site load and test all application programs in the processors and server; perform testing to verify all devices were communicating as intended.
Network Construction and Testing
In coordination with Malisko, corporate IT, and the network installation team, new fiber and copper runs were installed concurrently with production, before the cut over date.
2. DURING THE CUTOVER
Over 800+ I/O point were cutover to ControlLogix and powered on the first day of the commissioning window in addition the server and PLC installation.
Operational Testing and Coordination
Plant maintenance and operations staff assisted the Malisko Team to perform on-site operational testing as soon as each new I/O chassis assembly was in place, wired and powered.
Daily updates and punch list items were distributed between all parties involved including plant management.
3. AFTER THE CUTOVER
Malisko Provided onsite production support to assist the plant to startup production.
Remote Connectivity and Support
In coordination with corporate IT, a secure connection was established to provide Malisko with remote connectivity to the pant for future integration and troubleshooting assistance.
Assuring that all system programming and documentation was updated in addition to maintaining a quick project turnaround enabled better decision making for plant management.
Plant upgrade included new Rockwell Automation hardware and an improved network to provide Malisko and plant partners with remote connectivity to provide timely system support.
Want to learn more about this project or how we can help you with your manufacturing challenges? Simply fill out the form below and someone from the Malisko team will reach out to you shortly.
500 N Broadway
St. Louis, MO 63102
Western Regional Office
4600 S Ulster Street
Denver, CO 80237
Northern Regional Office
3610 Oakwood Hills Parkway
Eau Claire, WI 54701